In the past, the nuclear power industry has experienced equipment failures due to improperly set oilers. There was never a precision tool available to help ensure the level was being properly set on a typical oiler . . . until now.
When measuring vibration, one of the most important factors in obtaining accurate information involves selecting the proper vibration transducer. Selecting the wrong vibration transducer can yield results that are misleading or, worse, mask a problem.
PWM inverters introduce motor shaft voltages and bearing currents. The bearing damage in inverter-driven motors is mainly caused by the shaft voltage and bearing currents created by the common-mode voltage and its sharp edges . All inverters generate common-mode voltages relative to the power source ground that cause coupling currents through the parasitic capacitances inside the motor. The main source of bearing currents is the capacitance-coupling currents that return via the motor bearings back to the ground.
When the City of Delaware, Ohio, expanded its wastewater treatment plant, it looked to increase more than just capacity. It also wanted to increase its efficiency and automation capabilities to benefit the plant's operators and taxpayers.
Mechanical pressure gauges, which require no external power, provide an affordable and reliable source of accurate pressure measurement. Using the criteria below can help maximize gauge life.
Sensors and automation passively participate in our everyday lives to improve comfort, add safety and reliability, and increase the efficiency of needed products and services.
Changing traditional industry ways of thinking can help usher in the plant of the future.
In only a couple of years, the focus on energy efficiency has gone from blurred to steely-eyed. Green business practice is now a necessity, and organizations must find the best way to transition to this new reality. There are many opinions and approaches on "how we get there," and each one will have its own merits. A journey of a thousand miles starts with a single step, and making the right steps in the beginning will hasten the achievement of energy efficient goals.
Lubricated machines require clean, dry oil to work properly.
Soft starters and VFDs are useful for extending equipment life in HVAC applications.
Determining the correct maintenance strategy for industrial production assets poses a problem for many plant asset managers and reliability and maintenance engineers.
"An ounce of prevention is worth a pound of cure" may have been coined by process and plant engineers tired of repairing or replacing pumps. Pumps are often the most under-serviced pieces of equipment in process automation when it comes to maintenance and prevention best practices. Unfortunately, nothing moves without the humble pump, and a process becomes inefficient when a pump doesn't operate properly or completely shuts down. Many times the pump manufacturer is seen to be the problem, when in fact the process or the surrounding equipment configuration is the cause.
Last month we reviewed the pump selection criteria for a closed loop circulation system (Vp-Vf). This month we will take a look at a similar application that adds some elevation to the equation.
One of the major contributors to unbalance in rotating machinery is eccentricity. When we disassemble parts, we must also reassemble them. Even if the reassembly requires heating to shrink-fit the elements back together, we probably balanced them in a balancing machine where tolerances due to fit-up on mandrels or roundness of journals may possibly far exceed the heavy spot tolerances that the target standard of balance allows.
Pumps are sent to rebuilding and remanufacturing companies because buying new can be expensive and require long lead times. For instance, a 39 in diameter, 1,000 lb bronze impeller may cost $28,000 and take many weeks to deliver. In these cases, the impellers involved in an overhaul are often built back up to the required specifications and rebalanced.
Even when a redundant pumping system is in place, it can be advisable to monitor the condition of the operating units in critical applications where maintaining production depends on motor-pump reliability.
A dangerous misconception exists regarding the "Arc Rating" of infrared (IR) windows or viewing panes. Many reliability and maintenance professionals are under the impression that an IR window will protect them in the event of an arc blast. Others believe that installing IR windows will turn non-arc-rated switchgear or electrical equipment into "arc-rated" cabinets. Neither is true. Both misconceptions need to be corrected because they present safety concerns.
Interpretation of equipment clues can help diagnose problems before failure occurs
Many items must be considered when designing pump station control systems with power requirements, level control method and control panel location often among the most important.
If pump cavitation is not detected and quickly eliminated, significant damage can occur to the impeller and other internal components. Since cavitation (the formation and collapse of vapor bubbles in the pumped fluid as it passes through the pump impeller) is often temporary or even induced by the process, timely knowledge of the condition is extremely important so operators can act to alleviate the problem and prevent damage.
The installation of an AC drive with an advanced software tool has dramatically cut call-outs for blockages at an Irish county council pumping station.