Figure 2. Influencing factors for calculating pump efficiency for different configurations.
Figure 2 contains the factors needed to calculate pump efficiency for different configurations. A string test cannot measure the efficiency of an engine-driven pump. In this case, the pump would need to be tested separately if accurate shaft power measurements are required. The pump manufacturer's curves often only provide the end user with the required power at the pump input shaft. Further investigation may reveal that this information is provided with the pump being sealed by packing, not mechanical seals, which may absorb additional power. From an energy consumption standpoint, these data do not provide the user with the true cost to operate the pump.
Wire-to-water efficiency and power consumption curves are more useful but are rarely requested. Wire-to-water performance can be measured with all the configurations in Figure 2 by placing a wattmeter at the input to the motor or VFD. These data will allow the end user to know the true power consumption of the pump system and evaluate the true operating cost.