Answers to the industry's pressing technical and management questions
Q. When purchasing new rotodynamic pumps, what type of acceptance testing is recommended?
A. Purchasers of rotodynamic pumps should specify acceptance testing that will verify the rate of flow, head produced and power required. The costs of acceptance tests and special tests should be clearly stated in the contract. Specifying tighter acceptance tolerances can lead to higher testing costs and increased lead times. When NPSH testing is specified, test costs will be higher because the tested pump must undergo a different and more time-consuming test, often performed with a different test set-up requiring additional assembly and tear-down time.
|Figure 1. Recommended tests for different pumps and services|
For reduced tolerance bandwidth, tighter manufacturing tolerances are required, which adds cost and increases delivery time. Sand-cast molds are the least expensive but have the greatest tolerance. Investment casting techniques will provide superior surface finish and most consistent dimensions.
Molding equipment expense for an investment casting may be two to four times greater than a sand casting mold. A high production volume is needed to justify the additional expense of this equipment. Many hours of hand labor may be required to produce sand castings to tight, repeatable tolerances.
Machining parts to closer tolerances can increase the labor cost by 50 percent and increase the time to manufacture the part to the required tolerances. Reduced tolerances increases costs because of the additional care required during production and the potential of an increased scrap rate. The impeller may need to be hand-worked to obtain the required performance. Impellers must be axially positioned for optimum alignment with the casing to produce the required head and high efficiency.
Figure 1 should be used as a guideline. For normally manufactured pumps, users may consider a certificate of compliance instead of actual testing.
Q. What is a string test, and when should it be specified?
A. Generating a Pump Curve requires measuring the rate of flow, head and power. From this information, the pump efficiency can be calculated. The Pump Curve efficiency is typically related to the shaft input power. The published efficiency is the hydraulic power produced by the pump divided by the mechanical input power to the pump shaft. The efficiency published is only that of the pump. From a testing standpoint, the most accurate way to obtain the power data is by direct measurement of the shaft torque and rpm. This is done using a torque transducer and a tachometer. These values are used when calculating the power input to the pump.
A less accurate method, but one that may be specified, is a string test using the complete assembly—the motor, pump and drive (for example, gearbox, belt drive, etc.). The accuracy of this test will be lower than when the pump alone is tested. In this instance, the power measured is the input power to the motor. The input power to the pump shaft is calculated by using the published motor and drive efficiencies. Since these efficiencies are not known precisely, this method is less accurate.