HI Pump FAQs® is produced by the Hydraulic Institute as a service to pump users, contractors, distributors, reps and OEMs. For more information, visit pumps.org.
HI Pump FAQs
Q. How has the Industrial Internet of Things (IIoT) impacted the pump industry?
A. The pump industry has seen a growing trend to implement new technologies, based on the Industrial Internet of Things (IIoT) trend. They provide the original equipment manufacturers (OEMs) the opportunity to offer more to the purchasers and users. The Hydraulic Institute recently addressed wireless data transmission technology innovations in the latest revision of the ANSI/HI 9.6.5 Rotodynamic Pumps for Condition Monitoring standard.
Condition-based maintenance (CBM) is the monitoring of the output of various sensors and/or indicators. Machinery condition may be assessed by monitoring many indications, but vibration analysis has taken the forefront of implementing wireless data transmission. The level and pattern of vibration can indicate the health and condition of rotating components.
For specific markets, such as industrial sensors, wireless technology is evolving rapidly while standards are significantly lagging.
Proprietary wireless protocols that are specific to CBM sensors are expected to fulfill an important role in enabling wireless online monitoring at a comparable level to a wired solution.
The development of IIoT is expected to increase operational efficiency by up to 45 percent and provide a fairly quick return on investment (ROI) for manufacturers as a result of readily available diagnostic data capabilities.
Q. How can you implement the IIoT to monitor vibration in a pumping system?
A.Wireless vibration transmitters provide early indication of potential problems. Various problems in pumps can be detected using vibration monitoring, including bearing problems, imbalance or misalignment of rotating elements, gear tooth damage, loose connections of pump and motor components, and drive belt and coupling problems.
Vibration monitoring sensors are mounted on the bearing housing to detect these changes in vibration.
These sensors can be mounted permanently and monitored continuously or mounted temporarily as part of a route-based periodic monitoring system.
Data can be collected in multiple locations and directions (horizontally, vertically and axially) on the equipment. Vibration data is recorded and can be analyzed remotely or by program to identify faults.
There are several topologies for connecting a wireless sensor to a receiving station for data processing. Figure 22.214.171.124.1 shows the star topology network. The star topology is a network that consists of one central node, typically a switch or hub, which acts as a conduit to transmit messages.
Figure 126.96.36.199.1. Example of a vibration diagnostic system network (star topology) (Courtesy of Hydraulic Institute)
In this network for CBM, the primary receiver nodes (PRNs) communicate with multiple vibration sensor nodes simultaneously to collect vibration time data.
In turn, the PRNs connect directly to a database server computer or to a company’s network backbone via a collection server.
In effect, a sensor network is a two-level star with a database server computer at the center connected directly to the sensor network scales from a very simple two- to three-sensor network. This can monitor anything from the health of a single machine to a very large network with sensors on hundreds of machines.
Figure 188.8.131.52.1 shows how the collection server may be connected to a plant’s or facility’s network.
These include Ethernet connected directly to the company’s backbone intranet, a Wi-Fi or Bluetooth connection to a company’s existing wireless network, and cellular network data connection to the Internet via a cellular telephone carrier. This network infrastructure example highlights the benefits of wireless, online CBM strategies in terms of ease of installation and expandability/scalability.
Radio frequency (RF) wireless communication capability, including transmission range, reliability, and data throughput, pressure important trade-offs in performance and capability that are negotiated when applying wireless solutions to specific applications. For this reason, different wireless communication solutions have emerged to serve markets with different requirements. For example, Bluetooth is suited for pairs of devices that can communicate over short ranges, while WirelessHART enables large networks with low data rates. Wi-Fi supports high data rates but it is not suited for battery-powered operation.
For more information on vibration monitoring for pumping systems, refer to ANSI/HI 9.6.5 Rotodynamic Pumps for Condition Monitoring.
See other HI Pump FAQs articles here.