Rotary positive displacement (RPD) pumps theoretically displace a fixed amount of fluid per revolution. However, some loss in output is typically caused by the fluid slipping past the rotors. The difference between the quantity displaced (Qd) and the actual output quantity (Q) is slip (Sq). The volumetric efficiency of RPD pumps depends on the percentage of slip to the total quantity displaced. The total output quantity as a percentage of the quantity displaced is the pump's volumetric efficiency. The principle determinants of slip in the normal range of a pump's operation are:
- Viscosity—The higher the viscosity (V), the lower the slip.
- Pressure—The higher the differential pressure (Pd), the higher the slip. Pressure increases slip in pumps with flexible or compressible parts, such as flexible vane impellers or rubber coated lobes, more than in pumps with parts constructed of rigid materials such as steel.
- RPD pump type—Each pump type has different clearance requirements. For example, flexible vane pumps do not require any vane clearance whereas a rotary lobe pump with stainless steel lobes does require clearance from the housing. Within a pump type, some manufacturers are better able to meet tight clearance requirements with precision than others.
- Wear—As components wear, the clearances between them increase. At higher pressures and lower viscosities, this clearance difference may increase slip significantly.
Slip does not increase as pump speed increases, although the displaced quantity does increase. As a result, the faster a RPD pump is operated, the greater the volumetric efficiency, as illustrated in Table 1.
Unfortunately, operating an RPD pump at the upper end of its normal range may be counterproductive. High speed will produce rapid wear if the fluid is abrasive, creating greater slip with time.
Shear-sensitive fluids may be adversely affected by high pump speeds, even though RPD pumps are generally low shear. High pump speed operations may not provide enough time for highly viscous fluids to fill the pumping cavities completely. This will cause a reduction in the output quantity.
Testing High-Viscosity Fluids
A manufacturer of rotary lobe pumps (positive displacement rotary pumps) produces pumps equipped with nitrile rubber (NBR) coated lobes, although some are hydrogenated nitrile butadiene rubber (HNBR), fluorocarbon (FKM) and solid metal lobes. For many years, the manufacturer tested each pump in a test pond to ensure the pump met the published curve for flow and horsepower at the duty point for pumping fresh water, which is close to a viscosity of 1 centipoise (cP).
However, through 2013, this manufacturer had not tested the pumps to determine the effect of higher viscosities on output and horsepower (HP) in part because many of its customers were unable to supply the viscosities of their fluids.
For example, municipal sludge's viscosity depends on the temperature, percentage of solids, sludge type and how long the sludge has been stationary. The slip and HP required to move municipal sludge are typically estimated from practical experience based on the type of sludge and percentage of solids. With time and experience, however, many end users can provide the minimum and maximum viscosities of their fluids. Up to 2013, the manufacturing team estimated the effect of viscosity using Equation 1.
Slip is a function (K) of the differential pressure divided by the viscosity. The manufacturer estimated K based on other pumps' published data. By the end of 2013, however, the manufacturer decided to determine the effect by direct testing.
In 2014, the company's quality control manager and plant manager, under the supervision of the vice president of engineering, conducted extensive tests to determine slip using one of the manufacturer's rotary lobe pumps. The selected pump model had a displaced quantity of 34 gallons per 100 revolutions. The tested pump was equipped with new 70-durometer, NBR lobes.
The advantage of rubber-coated lobes is that they are compressible enough to permit a very close fit with the pump housing. This close fit permits the pump to create a strong vacuum that results in the ability to self-prime up to 25 feet. The compressible rubber coated lobes also allow the pump to pass small hard solids without damage. The disadvantage is that, under high pressure, the rubber coating will compress and increase slip.
The pump housing and wear plates are made from hardened metals. For all tests the pump was operated at 300 rpm at multiple differential pressures from 1 to 75 pounds per sqaure inch (psi). The test team used recently certified vacuum and pressure gauges to determine the differential pressure and recorded barometric and fluid temperature before each test.
At each psi level, multiple tests were conducted to determine the effect of the fluid viscosity on slip. The viscosity of the test fluid was determined by evaluating a 1-liter sample on the viscometer spindle. The viscosities tested ranged from 1 to 1,912 cP. Periodically, certified viscosity fluids were used to ensure that the spindle was properly calibrated.
The test team kept careful track of the barometric and water temperature throughout the testing process. However, when the team members conducted regression analysis of the data, these variables were not significant. The barometric pressure ranged from 29.86 to 30.22. The fluid temperature ranged from 12 to 22 C.