Editor’s note: This article provides additional information that further explains Ray Hardee’s monthly Pump System Improvement column appearing in the August 2016 issue. Click here to read it.
Figure 1 shows 12 circuits of a much larger cooling water system. Like all piping systems, the total system consists of the pump elements, process elements and control elements. Each circuit in the system has each of the three elements. To demonstrate, we will follow the circuit on the right side of Figure 1.
The circuit starts at the cooling tower, which serves as a pressure boundary and provides us with a location where the fluid energy is known. Because the cooling tower provides all cooling water for the system, it is shared by all the circuits in the total system.
Our example circuit continues from the pump discharge headers through a common supply header, then branches off to a common header for Area 51, where the system branches to process heat exchanger HX-101. Downstream of HX-101, the circuit continues with throttle valve TV-101. The throttle valve is positioned to set the rate through the circuit to the design flow rate. The circuit then proceeds through the various common return headers back to the spray header on the cooling tower.
In this system, the cooling water flow rate through each of the circuits is determined to remove the heat exchanger’s thermal load. This is accomplished using a temperature-control loop or by setting the position for all system throttle valves to a balanced position. The heat load in this cooling water system is constant so the system was designed using manually operated throttling valves.
A balancing contractor determined the position of each throttle valve by estimating a position to the throttle valve in each circuit. When the system was started, the flow rates were checked in each circuit within the system. In the circuits with flow rates less than the design value, the throttle valve position was increased. In circuits with flow rates greater than the design value, the throttle valve position was decreased.
What makes the process even more difficult is that changing the position in any circuit affects the flow rate through all circuits. As a result, the balancing contractor must arrive at a set of new valve positions after each pass and determine how they affect the flow rates through each circuit.
Early in my career, I was involved in manually balancing a cooling water system at a nuclear power plant. It took a team of more than 10 people about a week to balance the loads for all circuits to the designed flow rate indicated in the test procedure.
Recently, new loads were added to the cooling water system, and the flow rates through some existing loads were increased. As a result of the change in flow rate, the system was no longer balanced. After the addition of the new loads, the team decided not to employ the services of a balancing contractor. Once the cooling water system was placed in operation with the additional loads, the plant operators opened the throttle valves to increase the flow rate through the heat exchanger to maintain the proper outlet temperature. One thing the operators were not aware of is that each adjustment to a throttle valve in a circuit affected the flow rate in all circuits. As the operators continually adjusted the system, over time the flow rate through the system was much higher than the process requirements.
Figure 2 shows the pump curve for each pump when two circulating water pumps are supplying the system with all throttle valves fully open. Notice the flow rate through each pump is approximately 1,800 gallons per minute (gpm), overloading the motor. This resulted in the motor tripping on high current.
As described previously, the operators immediately started the standby cooling water system. After they determined that the pump tripped on high motor current, the operators placed the third cooling water pump in service.
With three pumps in operation, the flow rate through each pump was reduced, but because three pumps were now operating, the system flow rate was higher. Figure 3 shows how a single pump operates when all three pumps are operated.
The pump curve shows that the head developed by the three pumps operating in parallel is 165 feet, with a combined total flow rate through the system of 4,400 gpm. The flow rate through each pump is operating to the right of its best efficiency point (BEP), but well within the motor’s duty factor.