Q. What are some factors to consider when conducting a life-cycle cost evaluation for a sealless rotary pump?
A. There is a substantial first-cost premium for sealless rotary pumps. Depending on the type, this cost is a multiple of a similar pump with a conventional mechanical seal. A magnetic drive pump’s expense is primarily associated with the cost of the magnets required to transmit torque.
Sealless pumps may be selected for many applications based on a life-cycle cost analysis. Each application is subject to individual review, but general areas that may be considered in a life-cycle cost analysis are:
- Negative for sealless pumps
- Initial capital cost
- Additional instrumentation, if required
- Lower drive efficiency
- Variable cost elements based on user experience
- Cost of maintenance differential (numerous surveys have shown mechanical seal failure to be the primary cost of pump maintenance)
- Cost of production loss associated with system reliability
- Reduced cost of instrumentation compared to complex seal systems
- Positive for sealless pumps
- Monitoring exemption for fugitive emissions under the Clean Air Act
- Cost of liquid disposal as a result of seal failure
- Risk associated with personnel or fire incident loss
- Cost of alternate sealing systems to meet environmental emissions control requirements, such as double-seal and compliance
- Value of extended operating periods between unit turnaround
- Space reduction when compared to complex seal systems
- Cooling water costs
Economics may initially be difficult to assess until operating, maintenance and monitoring expense experience has been gathered. Records of these considerations are valuable to the pump selection process.
For more information about rotary sealless pumps, see ANSI/HI 4.1-4.6 Sealless, Magnetically Driven Rotary Pumps for Nomenclature, Definitions, Application, Operation, and Test.
Q. What are some baseplate designs and considerations for rotodynamic pumps?
A. Baseplate designs for rotodynamic pumps include the grout type and the non-grout type, among others. The grouted baseplate is designed to allow grout to be poured under the base. The grout placed inside the base contributes to the baseplate’s installed rigidity and damping. See Figure 126.96.36.199.1a.
Figure 188.8.131.52.1a. Grouted baseplate, fabricated steel
The cross members used on this type base are normally designed to lock into the grout to further resist baseplate deflection or vibration. Typically, the cross-member geometry chosen to achieve this is an L-section (shown in Figure 184.108.40.206.1a), a T-section or an I-section.
Figure 220.127.116.11.2. Non-grout baseplate
If the baseplate is a closed design (for example, grout cannot be poured inside the baseplate perimeter because of the presence of a drain pan or deck plate), then grout holes must be provided to allow the grout to be placed inside the base.
The grout used may be either cementitious or epoxy-based. The surface preparation required for a baseplate to successfully bond to the grout is different depending on which grout will be used. Therefore, the vendor and customer must agree in advance which type grout will be used.
The baseplate in Figure 18.104.22.168.1a is typical of a fabricated baseplate. Cast-iron baseplates are another example. The ability to integrally cast in features—such as bracing, grout holes and sloping surfaces—provides a highly functional and economical solution for many applications.
The non-grout baseplate is placed directly on a foundation without the use of grout to fill the interior of the base to lock it to the foundation. Because of the loss of stiffening normally provided by the grout, non-grout bases must typically be structurally stiffer than comparable grouted bases.
Cross members do not need to lock into the grout and, therefore, may be selected on the basis of providing the best stiffening effect. For this reason, hollow rectangular sections are often used in this design. The advantage of this design compared to a grouted design is simplified installation.
The structural design must be stiffer than an equivalent grout-type base. Additionally, the structural natural frequencies must be separated from any equipment operating frequencies. This is because the stiffening and dampening effects of the grout are not available.
The non-grout type is often used in offshore installations in which the mass of grout and concrete must be avoided. This type can be provided for all types of rotodynamic pumps. (A multistage, axial-split, between-bearings pump is illustrated in Figure 22.214.171.124.2).
For more information about other baseplate designs—including pre-grout, sole plate and freestanding—see ANSI/HI 1.3 Rotodynamic (Centrifugal) Pumps for Design and Application.
Q. What kinds of impellers are used in slurry pump applications?