The Eleventh in a Series
The Injection of Air to Reduce Noise and Damage
The gas may form a cushion to reduce the impact of collapsing vapor bubbles and/or may expand to act against the drop in pressure.
How Much Does an Inducer Reduce NPHR?
Some centrifugal pumps are available with a small axial‑flow or mixed‑flow impeller installed just ahead of the main impeller, as shown in Figure 1. Some are actually installed inside the eye of the main impeller.
Figure 1. A Horizontal Centrifugal Pump with an Inducer
An inducer will typically reduce the NPSHR of the pump (based on a 3 percent head drop of the combined impellers) about 40 percent at the BEP, but will require more NPSH than the main impeller at lower and higher capacities. (It reduces the range of operability of the pump.)
Inducers also normally cavitate continuously, so are subject to a short life when pumping cool water.
NPSH Requirements of a Reciprocating Pump
Why Does a Reciprocating Pump Require NPSH? What Units Should We Use?
In a reciprocating pump, NPSH is required to push the suction valve from its seat and overcome friction losses and acceleration head inside the liquid end. Because a significant portion of the NPSHR is required to open the valve (particularly at low pump speeds) and this is a pressure (rather than a head) requirement, NPSHR for a reciprocating pump is normally expressed in pressure units such as PSI. For example, if a power pump requires 2 psi of NPSH when pumping water (4.6 ft), it will require 2 psi of NPSH on propane (9.2 ft).
Because it is a pressure, some reciprocating pump authorities use symbols for the NPSH characteristic such as NPIP (Net Positive Inlet Pressure) and NIP (Net Inlet Pressure). For simplicity, we will stick with NPSH, regardless of the units used for the quantity.
NPSHR Curves of a Triplex Pump
A study of Figure 2 will provide a better understanding not only of reciprocating pump NPSHR, but also of valve action. These curves are for a 3 in stroke, horizontal, triplex plunger power pump with suction valves that operate vertically. The valves are wing‑guided, each having a seat flow area approximately equal to the plunger area.
Figure 2. NPSH Requirements for a Triplex Plunger Pump